Explore Lightning Protection Using LFA-M with Free Download of Seminar Report and PPT in PDF and DOC Format. Also Explore the Seminar Topics Paper on. The important feature of this modular long flashover arrester (LFA-M) is that it can be applied for lightning protection of overhead distribution line against both. Presentation on theme: “LIGHTENING PROTECTION USING LFA-M”— System ”-A system of lightning protection conductors lightning rods -installed on the.
|Published (Last):||12 June 2009|
|PDF File Size:||20.16 Mb|
|ePub File Size:||10.11 Mb|
|Price:||Free* [*Free Regsitration Required]|
When the potential between the cloud and line exceed the breakdown value of lightning protection using lfa-m, the lightning discharge occurs between the cloud and the line. Thus, the number of outages caused by direct lightning strokes can be lowered with the use of LFA arresters by an order of magnitude or more even for high values of grounding resistance.
How lightning is formed. If you wish to download it, please recommend it to your friends in any social system. Types of lightning II. Due to different propagation rates of flashover channels lightning protection using lfa-m lightning impulses of positive and negative polarity, the first module to flashover is module 1 with a flashover. When the modules increases the total arrester stressing is distributed these modules also.
From the line, current path may be over at the ground.
Lightning Protection Using LFA (Lightning Frequency Arrester)
The induced positive charge leaks slowly to earth. The induced over voltages can be counteracted by installing a single arrester on an overhead lightning protection using lfa-m support pole. When cloud discharges to earth, -ve charge rushes along both directions in form of lightning protection using lfa-m wave. For the protection of lines against direct lightning strokes, the arresters are connected between the poles and all of the phase conductors in parallel with the insulators.
In stroke B the lightning discharge occurs on the overhead line as the result of stroke A between the clouds. Indirect stroke result from eletrostatically induced charges on the conductors due to the presence of charged cloud. An LFA-M arrester consists of two cables like pieces.
LIGHTENING PROTECTION USING LFA-M
Automatically changes to Flash or non-Flash embed. Therefore, in order to protect the line against the direct lightning stroke.
An LFA mounted on the top phase must flash over usingg lightning protection using lfa-m top phase insulator. The over voltage set up due to the stroke may be large enough to flashover this path directly to the ground. The direct stroke can be of two types 1.
It is designated as LFA-M.
How does LFA-M protect the oightning lines?: The above calculation does not take into account the effect of near-by poise: Can be applied for protection of distribution lines. Pole-top arresters were lightning protection using lfa-m to protect distribution line from induced voltage flashovers.
Static electricity is the accumulation of excess electric charges on an object. Lightning is an electrical discharge between cloud and the earth, between clouds or between the charge centers of the same cloud. The arresters are connected between the pole and all of the phase conductors in parallel with the insulators. Lightning is a huge spark and lightning protection using lfa-m take place when clouds are charged to at a high potential with lightning protection using lfa-m to earth object e.
Are you interested in this topic. Semiconductive core of upper piece, whose resistance is R ,applies the high potential U to the surface of the lower piece at its middle. Extend the working life of high voltage circuit breakers. Therefore, the nearest pole is not to be taken into account in the coordination lightning protection using lfa-m of the LFA A. Therefore, this arrester should be relatively short. Devices which capture the high voltage sparks resulting out of lightening.
The pole does not get involved in the path of the lightning current until the insulator or the usig have flashed over. A ,fa-m long flashover arrester model has been developed. We think you have liked this presentation. As indicated before, the coordination of arrester LFA A is not depend on the grounding resistance because The pole does not get involved in the path of the lightning current until the insulator or the arrestors have flashed over.
The probability of PAF sharply decreases with a decrease in E. With one or both outer phase arresters activated, a two or three phase lightning flashover is initiated.
It keeps increasing at a still slower rate until time t 3. The cable pieces are arranged so as to form three flashover modules 1,2,3 as shown in figure1. Tests have been shown that, lightning protection using lfa-m the line conductor is stressed by lightning over voltage impulse, flash over channel develop at different rates.
Each cable piece has a semi conductive core lightning protection using lfa-m resistance R. This is the reason why the calculation takes into account the critical values of the lightning current steepness Lightning protection using lfa-m l l ,cr at which the insulator flashes over for a given set of parameters. Direct stroke Indirect stroke. For a lightning stoke on a phase conductor, the lighting current propagates both ways from the stroke point overcoming the surge impedance Z s of the line.
Unit 4 Ch Posted by Sagar at 4: